# E-coil control: Resonance curve procedure – Location curve procedure

Info Letter No. 12

#### Compensated Networks

In “compensated networks” the current through the point of failure is minimised with the help of an earth fault compensation coil (e-coil). For this purpose, the e-coil is already in operation in a healthy network, i.e. set without an earth fault so that in the event of an earth fault, the capacitive component of the current is compensated by an inductive current through the fault location. The following figure, Figure 1, shows the network in the case of a single-pole earth fault in Phase L1.

Lp
C1, C2,C3
ZF
N
E1,E2,E3
Uo
IC1, IC2
ILP
IW
IF

E-coil (Petersen coil)
Conductor capacitances of phases L1 to L3
Transmission impedance at the fault location
Neutral point of the transformer
Phase voltages
Zero sequence voltage
Capacitive currents in both healthy phases
Inductive compensation current through the e-coil across the fault location
Active component
Current across the fault location

#### Objective of the E-Coil

The objective of the e-coil control is now to set the e-coil in the healthy network operation to the desired value already. Several methods are available for the control, wherein the equivalent circuit for the resonance procedure and the location curve procedure can be derived without the use of symmetrical components.

#### Simplified equivalent circuit

The simplified equivalent circuit diagram should describe the network in the range from the operating state “healthy network” to the operating state “saturated earth fault”. First, for a simpler notation, the capacitances of the network and the inductance of the e-coil are replaced by their complex conductances (admittances). It is assumed that the resistive or capacitive asymmetry in the case of an saturated earth fault is present in only one phase.

Contact

## News from the product group

### EORSys - News

General Knowledge

#### Earth fault explained – basics and functions of an electrical phenomenon

Everything you need to know about earth faults - from the basics, causes and examples to the consequences. Find out more in this article about earth fault clearing, compensation, location and the benefits of constant monitoring to ensure a safe power grid.

Info letter

#### Info Letter No. 21: The influence of the contact resistance at the earth-fault location on the zero sequence voltage UEN in compensated networks

The earth fault in compensated networks is usually presented without a contact resistance at the fault...

Info letter

#### Info Letter No. 20: Capacitance of conductors

In the conductors of electrical power supplies, a distinction is made between the operating capacitance...

Info letter

#### Info Letter No. 4: Summation of Alternating Currents

For the parallel connection of power sources, the principle of superposition applies, when all resources...

Info letter

#### Info Letter No. 3: The E-coil in general

The earth fault compensation coil, e-coil or also called the Petersen coil after its inventor, is connected...