Motorway rest stop pilot project
Power cuts shut down water pumps and pose great challenges for the North-Bavarian motorway directorate.
In 2018, the “Auergründel” PWC (car park with WC) on the A6 suffered repeat failures of its fresh and waste water pumps. The motorways directorate suspected the cause was high loads on the low-voltage cables. The short-circuit power of the network at the parking place was suspected to be insufficient to provide stable pumping.
What we did
Through a power quality (PQ) measurement with our PQ-Box 150, we determined that the 10 minute voltage averages were below the nominal voltage. This allowed us to determine that, when the pumps started up, the voltage at the connection point collapsed to the point that the frequency converter switched to error mode and reported an undervoltage. Increased power requirements during start-up can be compensated for by our low-voltage regulation system LVRSysTM, which provides increased current.
Since the installation of the LVRSys, no further faults in the control electronics have been reported. LVRSysTM solves problems at motorway car parks like “Auergründel”, thus preventing the failure of gantry signage, water pumps and lighting systems at parking spaces and rest facilities.
You can find the detailed application report here (German and English).
Cost efficient management of digital secondary substations: Earth fault indicator EOR-3DS as digitisation unit for secondary substations
Digital secondary substations are becoming a key element for distribution system operators in terms of automation, monitoring, and efficient operations of their networks Read this technical report about the EOR-3DS in its role as digitisation unit for secondary substationsRead more
Angle determination of voltage and current harmonics in practice
Tracking down causes of harmonics in the energy grid in practice Today, there are hardly any consumers that draw a […]Read more
All „Supra“ with your grid?
Today’s devices and equipment such as switched-mode power supplies, frequency converters, controlled drives, charging devices for e-mobiles or LED lighting work internally with high clock frequencies in order to regulate power efficiently. These can lead to line-borne as well as field-borne (coupled) interference in the power grid. In this technical report, we explain how you can detect these sources of interference in the grid using suitable measurement technology.Read more
Power Quality Analysis: Tips and Tricks II
Useful tips & tricks for handling Power Quality measuring devices and typical user errors – now in our two-part article! This article provides further insights and practical tips and application examples for power quality analysis.Read more