# Power Quality Measurements:

The Third Harmonic

The report “The N conductor & Harmonics” already explained the special features of the The report “The N conductor & Harmonics” already explained the special features of the harmonics divisible by 3 and why they add up on the neutral conductor. This special publication intends to illustrate a typical power quality measurement and the aspects, which should be taken into consideration conducting the measurements. The measurements displayed in this report took place in an office building where increasing problems with the power quality were detected.

#### If power quality problems occur, an evaluation according to IEC 61000-2-2 is necessary

Figure 1 shows an evaluation generated from our WinPQ mobile software. This evaluation represents a one-week measurement according to EN 50160/IEC 61000-2-2 in the grid of an energy supplier at a handover point to a larger office building. Measuring all parameters according to EN 50160, more than 500,000 values are recorded, which are statistically processed by the WinPQ mobile software. Since some devices in this office building are overloaded and fail after a short period, the tenant of the office building ask for an evaluation of the cause of this problem. In this diagram, all measured values are shown scaled to the compatibility values according to EN 50160. All bars that are below the limit line are uncritical. The values for voltage harmonics on phase L1 and L3 exceed the limit values and therefore further investigations should be conducted. However, this chart does not provide the required information to evaluate which frequencies have led to a limit value violation. Further data evaluation is required.

#### The examination of limit values is essential for the evaluation of power quality problems

Taking a closer look at the limit values of the individual harmonics as in Figure 2, three peculiarities stand out:

1. The 15th harmonic is violated on phase L1.
2. On phase L2 the value is still just below the compatibility values.
3. The value of the 15th harmonic is violated on phase L3.

As already described in the previous article, the odd-numbered harmonics 21, 27 and 27, which are divisible by three, also stand out

#### The excact date of the limit exceedance gives important information about the cause of the problems

By considering the gathered knowledge, the next step contains a check at which times the violation of the limit values took place. At this point, it is essential that the measurement runs over a week, even though there is no activity in the office building at the weekend. Scaling the data of the 15th harmonic to a week, the data suggest that the levels are at the same low level during the weekend and during the night. From Monday morning the levels rise somewhat and fall again towards evening. By setting markers on the high and low points, the evaluation software shows that the levels are elevated between 06:50 and 16:40 – the typical office hours when employees are in the building

#### The current harmonics give a hint about the location of the problems

By investigating the currents, it could be detected if the disturbance is caused in front of or behind the measuring point. If the office equipment with all the appliances is the cause of the harmonic, this the current harmonic could help to detect this fact. So, in addition to the 15th voltage harmonic, the 15th current harmonic should also be investigated. Figure 4 displays, that the neutral conductor is the highest load and corresponds approximately to the sum of the three phases. The 15th current harmonic, divisible by three, adds up on the neutral conductor. Taking a closer look at the weekly profile, direct correlations with the voltage curve can be ascertained: The higher the current harmonics, the higher the voltage level in the grid. This effect can also be seen with other harmonics. Unlike the current levels, one cannot assume that the voltage levels will drop to zero, because the voltages or feedbacks are the sum of all the consumers working in the grid, and at the weekend a large number of consumers are certainly active. Even a transformer in no-load operation produces some harmonics. With view at the limit values, it could be said that they are not exceeded at night and on weekends. Only during operating hours in the office, when many single-phase consumers are operated, the limit levels are exceeded.

#### The limit value evaluation is very simple using the WinPQ mobile

For users of the WinPQ mobile, there are also several different display options for the values. Figure 5, for example, shows the deviation of the measured value from the corresponding compatibility value in %. Of course, much smaller limit values apply to a 15th harmonic than to a 5th harmonic. Using the WinPQ mobile software, however, it is no problem to have the absolute values displayed in volts, as can be seen in Figure 6. In this figure, the 15th harmonic is not noticeable at all, but to note a limit violation, the user needs to know all limit values for each harmonic.

#### Conclusion

This measurement proved the customer’s influence on the increased voltage reading of the 15th harmonic. Due to the many single-phase consumers in this office building, the limit value was exceeded. Actions were taken to improve the power quality in the customer’s building.

Author
Jürgen Blum, Product Manager Power Quality Mobile

Contact

## News from the product group

### PQMobil - News

General Knowledge

#### Voltage Monitoring

Find out everything you need to know about voltage monitoring in this article. What is voltage monitoring, why is voltage monitoring essential for both energy supply companies and industrial companies and how is it implemented in compliance with standards?

General Knowledge

#### What Is Load Profile Measurement/Power Measurement?

This article explains the definition and difference between load profile measurement (RLM), power measurement and measuring the standard load profile. These are important methods for accurately recording energy consumption in commercial, large industrial plant as well as in the public energy grid.

Training Video

#### »PQMobil« Training Video 4: Create and Configure PQ Reports With Software WinPQ mobil

This video explains everything about creating and configuring power quality reports with »WinPQ mobil«.

Training Video

#### »PQMobil« Training Video 3: Usability & Functions of the PQ-Box App

This video gives you an introduction to the usability and functions of the »PQ-Box App« for our portable power quality analysers.

Training Video

#### »PQMobil« Training Video 2: Menu Navigation and Operation of the PQ-Box

In this short introductory video, we present to you how to navigate and operate our portable power quality analysers »PQ-Box 150«, »PQ-Box 200« & »PQ-Box 300« of the PQ-Box family.

Training Video

#### »PQMobil« Training Video 1: Getting Started with the PQ-Box

This video shows in detail how to connect the »PQ-Box« and record measurements. The »WinPQ mobil« software is then used to visualize and analyse the measurement data and create a report.

General Knowledge

#### Residual current

In this article, you will learn about residual current measurement & residual current monitoring and why it is important to measure residual current.

General Knowledge

#### Power Quality

Good power quality is characterized by the fact that the mains voltage actually arriving at the consumer matches the mains voltage promised by the utility company.

General Knowledge

#### Reactive power – definition, calculation and measurement

The key role of reactive power in electrical engineering: definition, calculation, measurement and the differences to active power and apparent power. Find out how reactive power influences the efficiency of electricity grids and shapes energy transmission.

General Knowledge

#### What is apparent power and how is it calculated?

This article addresses the question of what apparent power is and how to calculate it. An understanding of apparent power is crucial for the correct dimensioning of inverters and therefore for the optimum efficiency and performance of photovoltaic systems.

Info letter

#### Information Letter No. 24: Integration guide for the metering of a power plant according to the Requirements for Generators (2016/631) RfG

Integration guide for the measurement of a power plant (EZA) according to VDE-AR 4110 and VDE-AR 4120.

Info letter

#### Info Letter No. 23: Direction of harmonics Sources of harmonics in the power system

Le sens du flux de puissance des harmoniques est déterminé par le signe de la puissance activ

Info letter

#### Info Letter No. 22: Definition of power measurements according to the standards DIN 40110-2 and IEEE 1459

There is a wide range of electronic measuring devices for the digital measurement of power...

Info letter

#### Info Letter No. 20: Capacitance of conductors

In the conductors of electrical power supplies, a distinction is made between the operating capacitance...

Info letter

#### Info Letter No. 19: The evaluation of power quality and detection of interference in medium voltage network

For various reasons, interest in the continuous monitoring of network quality in medium-voltage...

Info letter

#### Info Letter No. 8: Apparent power and reactive power in three-phase networks

The range of electromechanical and electronic measuring devices in analog - and digital technology...

Info letter

#### Info Letter No. 5: Zero sequence voltage in three-phase networks

With balanced network operation and inequality of the impedances in the consumer circuit, the phase...

Info letter

#### Info Letter No. 4: Summation of Alternating Currents

For the parallel connection of power sources, the principle of superposition applies, when all resources...

Info letter

#### Info Letter No. 2: Measurement Transformers in three-phase networks (Part 2)

In a symmetrically loaded three-wire three-phase network, a two-pole insulated voltage transformer...

Info letter

#### Info Letter No. 1: Measurement Transformers in three-phase networks (Part 1)

The direct connection of measuring devices into the network is limited for safety reasons to values...

Webinar

#### »PQMobil« Webinar: Grid Analysis in Public & Industrial Power Grids with A. Eberle PQ-Boxes

Webinar recording from 2024-02-22: »PQMobil - Grid Analysis in Public & Industrial Power Grids with A. Eberle PQ-Boxes«.

Special Publication

#### Ferrari´s Meter vs. Electronic Meter

This technical report analyzes a power measurement at a large industrial customer. The customer records very high currents and fifth harmonic voltages during production time, which leads to poor voltage quality.

Special Publication

#### Angle determination of voltage and current harmonics in practice

Today's devices and equipment such as switched-mode power supplies, frequency converters, regulated drives, charging devices for e-mobiles or LED lighting work internally with high clock frequencies in order to regulate power efficiently. These can lead to both conducted and field-bound (coupled) influences in the energy grid. In this technical report, we explain how you can detect these sources of interference in the grid using suitable measuring technology.

General Knowledge

#### All „Supra“ with your grid?

Today's devices and equipment such as switched-mode power supplies, frequency converters, controlled drives, charging devices for e-mobiles or LED lighting work internally with high clock frequencies in order to regulate power efficiently. These can lead to line-borne as well as field-borne (coupled) interference in the power grid. In this technical report, we explain how you can detect these sources of interference in the grid using suitable measurement technology.

General Knowledge

#### Power Quality Analysis: Tips and Tricks II

Useful tips & tricks for handling Power Quality measuring devices and typical user errors - now in our two-part article! This article provides further insights and practical tips and application examples for power quality analysis.